Indian Journal of Science and Technology
Year: 2012, Volume: 5, Issue: 5, Pages: 1-9
S. A. Hosseini1 , F. Razavi2*, M. Karami3 , A. A. Ghadimi4 and S. S. Karimi Madahi5
1, 3,Department of Electrical Engineering,
2*Department of Electrical Engineering, University of Tafresh,
4Department of Electrical Engineering, Science and research branch,
5Department of Electrical Engineering, Islamic [email protected]1
[email protected]* 2 ,[email protected], [email protected],[email protected]
*Author For correspondence
Department of Electrical Engineering
Email: [email protected]
lightning arrester. Nonetheless, many SiC lightning arresters in Iran's electricity networks are operating. For instance, all the medium voltage network lightning arresters of Bakhtar Regional Electrical Company (BREC) are SiC type. The company wants to exchange these lightning arresters, but due to high cost and numbers of these lightning arresters, it is decided to put them in suitable ranks up to a due time. Since all suggested tests for recognition of lightning arresters deficiency are laboratory tests and must be done in lab, it isn’t possible for the company to transfer all lightning arresters from substation to lab. Therefore, it has been decided to carry out that in the substation. Accordingly, a project has been suggested and carried out by the writers of this paper and the present paper is the result of this project. Different theories in this paper are surveyed. DC test is introduced as a suitable way for correct recognition deficiency of lightning arresters. The acquired results of DC test on some samples of lightning arresters are in coordination with the standard tests that have been carried out in Pars High Voltage Lab. Finally, three groups of arresters are defined according to their operating condition which includes acting good, delayed acting and not operating arresters. According to this classification, BREC is capable to exchange the arresters with respect to condition of the related arrester and with an appropriate priority which is obtained from its condition.
Keywords: SiC Lightning arrester, Electricity network
Subscribe now for latest articles and news.